Water treatment inclined plate packingProduct Categories:
Environmental protection materials and pharmaceuticals / fillers
Full plastic "ethylene-propylene" honeycomb inclined pipe purifier The hexagonal honeycomb packing produced by our factory has two forms: inclined pipe and straight pipe. There are two kinds of materials: polypropylene and glass steel. The inclined pipe is mainly used for various sedimentation and sand removal functions. It is the most widely used water supply and drainage project in the past ten years and has become a water treatment device. It has the advantages of wide application range, high processing effect and small footprint. It is suitable for sand removal at the water inlet, general industrial and domestic water supply sedimentation, sewage sedimentation, oil separation and tail tension concentration, etc. It is suitable for new construction and retrofit of existing old ponds, and can achieve good economic benefits. Main features: 1. Large wet perimeter and small hydraulic radius. 2. The laminar flow is good, and the particle sedimentation is not disturbed by turbulence. 3. When the length of the inclined pipe is 1 meter, the effective load is designed according to 3-5 tons / meter2 · hour. VO is controlled within the range of 2.5-3.0 mm / s, and the effluent quality is the best. 4. The glass fiber reinforced plastic honeycomb inclined pipe is used at the water intake. When the pipe length is 2-3.0 meters, it can be safely operated and processed in the high turbidity of 50-100 kg / m3 mud and sand content. 5. The slant tube sedimentation tank adopts 3-5 times the capacity of the advection sedimentation tank, and accelerates the clarification tank and the pulse clarification tank by 2 times. > Technical parameters List of inclined pipe (plate) packing technical parameters (reference) Item Hexagonal honeycomb inclined pipe packing Sloping plate packing material PP ethylene propylene copolymerized PVC polyvinyl chloride FRP glass steel PP ethylene propylene copolymerized PVC polyvinyl chloride FRP glass fiber reinforced plastic Common specifications mm Æ35 Æ50 Æ80 Æ35 Æ50 Æ80 Æ35 Æ50 Æ80 35 50 80 35 50 80 35 50 80 Regular pieces / m2 42 32 20 42 32 20 42 32 20 27 19 12 27 19 12 27 19 12 Common piece thickness mm 0.35 0.45 0.65 0.35 0.45 0.65 0.3 0.5 0.7 1-2 1-2 1-2 1-2 1-2 1-2 1-2 1-2 1-2 Reference weight kg / m2 21 16 16 31 23 23 41 31 31 33-66 23-46 15 -30 50-100 35-70 23-46 65-130 45-90 30-60 Single piece size mm 1000 × 1000 × δ 1000 × 1000 × δ 1000 × 1000 × δ Customer-defined mm 1000 × 1000 × 866 1000 × 1000 × 866 1000 × 1000 × 866 Customer-defined Customer-defined Customer-defined products Application water, reclaimed water, sewage water supply, reclaimed water, sewage water supply, reclaimed water, sewage water supply, medium Water and sewage appearance color milky sky blue free custom milky gray free custom molding method electric iron ironing adhesive sticky plastic welding plastic welding adhesive Product installation site hot welding site bonding site bonding site welding site welding site welding installation angle of installation 60 ° 60 ° 60 ° 60 ° 60 ° 60 ° low cost high middle low Use temperature 5 ～ 80 ℃ 5 ～ 50 ℃ 5 ～ 70 ℃ 5 ～ 80 ℃ 5 ～ 50 ℃ 5 ～ 70 ℃ Specific gravity g / cm3 0.92 1.35 ～ 1.46 1.8 0.92 1.35 ～ 1.46 1.8 Features Flexible, easy to float Aging, brittleness, slightly toxic and acid resistance, alkali and acid resistance, alkali resistance, beautiful and slightly toxic acid and alkali resistance, production methods, factory prefabrication, factory prefabrication, factory prefabrication, site production, factory prefabrication, conventional packaging, strapping, bare packaging, strapping, bare packaging Bundled bare bulk bulk bulk shipping form bulk bulk bulk bulk bulk bulk bulk bulk bulk bulk shipping> Attention 1. As the specific gravity of the inclined pipe filler is 0.92 slightly less than water, Æ10mm rebar or round The steel reinforcement is fixed above the filler to prevent it from floating and floating, and the steel bars and angle steel are epoxy corrosion-resistant. 2. The A plate shown in the figure must be installed, otherwise the inclined pipe packing may be easily inclined or even collapsed! > Installation procedure 1. The installation of sludge pipe at the bottom of the sedimentation tank The installation sequence of the slanting pipe sedimentation tank generally starts from the bottom, and the installation of the bottommost sludge pipeline system is completed first to ensure that the opening of the sludge pipeline meets the design requirements, is firmly fixed, and is correct Only then is it allowed to proceed to the next installation process. Complete the installation of the filler bracket According to the installation drawing of the installation of the filler bracket of the inclined tube sedimentation tank, first install the filler bracket in place, check that all welding joints are firm, that the bracket is strong enough to bear the filler weight, and complete the anticorrosive treatment on the surface of the bracket; Pipe filler ironing According to the method of oblique pipe filler, each oblique pipe filler is packaged as a separate ironing unit. After a unit is ironed, it is 1m2. After the ironing is completed, it is neatly stacked on the site (retain a small amount of loose pieces) spare). Fourth, the assembly in the inclined tube filling pool Assembly of the filler unit after the ironing from the left to the top of the filler bracket assembly. Always keep the angle of 60 ° unchanged. Each unit should be properly compressed when it is assembled in sequence. If the size is not right when assembled to the far right, it needs to be soldered with loose-sheet oblique tube filler according to the size and assembled until it is in place. 5. The upper part of the inclined pipe packing is fixed. Because the specific gravity of the inclined pipe packing is 0.92, which is slightly smaller than water, the inclined pipe packing needs to be pulled up by Æ10mm round steel from left to right above the packing after being assembled in place in the tank (requires the upper part of each unit packing). There are two round steel bars passing through). The two ends of the round steel bars are reliably fixed on the wall of the sedimentation tank. After the round steel bars are installed, the loose and floating phenomenon that may occur during the initial use of the inclined pipe filler is well prevented. Coal tar anticorrosion. Operation and commissioning of the inclined tube sedimentation tank 1. Check whether the water inlet is uniform and should not cause impact on the sedimentation tank and affect the sedimentation effect; 2. Adjust the height and level of the weir trough to an appropriate level to keep the water uniform; The above construction procedures have so far completed the installation of the filler of the inclined pipe sedimentation tank. After normal use, the sludge cycle needs to be determined according to the concentration of suspended solids in the input water. Pay attention to the timely drainage of sludge to ensure that the inclined pipe sedimentation tank always maintains a good operating state and satisfactory effluent water quality.